Providing Expert HVAC Services in Johnstown, Ohio
Johnstown is a village in Licking County, Ohio. Located 18.8 miles northeast of Newark, Johnstown is part of a four-thousand acre piece of land deeded to John Brown in 1800. The village spans 2.9 square miles. Roughly 5,000 residents call Johnstown, Ohio home. Johnstown is the western trailhead for the T.J Evans bike trails, it’s a scenic 15-mile ride to Newark. Visitors can enjoy Johnstown’s local shopping boutiques and vineyards. We here at Newark-Heath Heating & Cooling are honored to provide our services to the citizens of Johnstown.
Newark-Heath Heating & Cooling is proud to be part of the Newark and Heath communities. With our stress-free and quick scheduling options, we are here to help you. Call us today at (740) 212-5849 to speak to one of our friendly customer service representatives, or schedule online with our convenient online form and we’ll contact you shortly to schedule an appointment. We look forward to providing you with the best HVAC services in the community.
Make an Appointment
Let our skilled HVAC experts help you today!
Instant Online Estimate
Get a quick and easy HVAC quote!
for Johnstown, OH
Great service after the call back
Mike - Johnstown, OH
Just a small issue with the fans not shutting off once the technician left. After he came back, all is good.
Carl was was very fast and knowledgeable.
Brent - Johnstown, OH
Great service quick and on time
Rusk - Johnstown, OH
Charlyn - Johnstown, OH
Technician was awesome. Knowledgeable, helpful. Did an excellent job.
Upon arrival customer stated furnace was not heating the home. Upon initial inspection of the gas furnace found that it was out on code 14 ignition proving failure. Referred to code 35 showing flame sensor with corrosion on it and carbon buildup not sensing the flame or not sending the proper amount of millivolts back after checking the flame sensor found it was quite a bit of carbon buildup in deposit on the sensing probe. Cleaned flame sensor off And inserted plane sensor back in the furnace cycled furnace back on let furnace run for 10 minutes and performed combustion test combustion test was 95% efficient 10.1% O2 15 ppm CO. And 96° flu Temp.System running and operating normal upon departure recommend April Aire media filter for better airflow throughout the home. Also recommended Honeywell t10 thermostat with room sensor to help with the temperature difference upstairs
I arrived to a diagnostic service call. Upon arrival customer stated that two rooms upstairs were colder than the rest of the house. I cycled the system and confirmed that filter is clean, blower speeds are set correctly and on the highest setting, and system is functioning properly. Upon further inspection I found that 2 supply runs at the furnace are closed off. Master bedroom vent is clear of debris, but second bedroom register was closed. Opened supply dampers, opened second bedroom register and recommend fan on the on position at thermostat. Explained to customer that I have done all that I can at this time. Next steps would be to update thermostat to one with sensors. System is heating properly upon departure